Failures after setup

- Failures after setup

-Battery issues

-Connectivity

-Wifi password, network name, or router changes

-Marginal connectivity/flapping

-Weather-related (buried in snow, ice, etc)

-Hardware failures

-Lots more in hardware failures that should be cataloged How to remove the sensor from the dial
 * Reading suddenly jumped to 0 - cable severed.
 * Reading jumped to 100 - likely a battery failure (with many potential causes)
 * Reading has stayed at 80 (or any number) but we’ve been using propane - float gauge might be stuck, check what the dial reads.

The sensor reads between 51 and 48 when not connected to the dial.